- Tech info of R410A
AVERAGE COP 10 at Air 26℃/ Water 26℃/ Humidity 80%
(COP means Coeffcient of Performance, it is a ratio of heating capacity to power consumption)
Half running cost principle (in 180 days swimming season)
In the first 5 days a Inverter-plus Commercial pool heat pump runs at 100% capacity and heats up the pool to the set temperature. In the next 175 days it runs at AVERAGE 50% capacity by AVERAGE COP 10 to maintain the desired pool temperature. So the AVERAGE COP is double of On/Off heat pump.
• Super Silent
AVERAGE 10 Times Quieter
When maintaining pool temp at AVERAGE 50% capacity, it brings a quieter swimming environment with twin-rotary DC-inverter compressor and unique ventilation system.
• Long Working Life
Low speed running philosophy extends working life.
• Soft Start
When Inverter-plus Commercial pool heat pump turns on,the current will start from 0A and go up slowly to rated current in 2 minutes. It will not affect the house electricity system, while the frequent start current of On/Off heat pump is 5 times of rated current, it is a burden to the electricity system.
|Advised pool volume (m3)||130~260||260~520|
|Operating air temperature (℃)||-7~43|
|Performance Condition: Air 26°C, Water 26°C, Humidity 80%|
|Heating capacity (kW)||60.0||110.0|
|COP at 50% capacity||10.1||10.0|
|Performance Condition: Air 15°C, Water 26°C, Humidity 70%|
|Heating capacity (kW)||40.0||81.0|
|COP at 50% capacity||6.8||6.8|
|Heat exchanger||Spiral titanium tube in PVC|
|Power supply||400V/3 Ph/50Hz|
|Rated input power at air 15°C (kW)||2.20~8.05||4.69~17.6|
|Rated input current at air 15°C (A)||3.17~12.0||6.77~25.4|
|Net dimension LxWxH (mm)||1000x1110x1260||2100×1090×1280|
|Net weight (kg)||212||459|
|Qty per 20'FT / 40'HQ (sets)||8/18||4/9|
←Please drag to see more on small size devices→